Product was successfully added to your shopping cart.
What is Circuit Breaker Testing used for?
Circuit Breaker Testing is used to test both the performance of individual switching mechanisms and the timing of the overall tripping system. Circuit Breaker Testing is essential to ensure the safe and reliable performance of this key link in the power asset chain.
Quick and easy to perform on site
Circuits can be tested on or off load
Tests performance of whole tripping cycle
Tests overall timing of tripping system
Identifies need for lubrication of maintenance
Circuit breakers perform a vital role in protecting expensive equipment from damage through power surges and faults. Testing the performance of your circuit breakers regularly is therefore an essential and cost-effective strategy.
What does Circuit Breaker Testing consist of?
Quad Plus Breaker Labs Circuit Breaker Testing service consists of two tests to assess the condition and performance of the tripping system:
Breaker Trip Test – Tests the performance of the various elements of the tripping cycle to identify and eliminate potential performance problems.
Secondary Injection of Over Current Relays – Tests overall protection timing to provide a report on protection performance at specified relay settings.
Electrical Testing Solutions offers complete Relay Testing Services. This includes well defined visual and mechanical inspections as well as electrical tests that ensure optimum service standards. Further, our process expertise also allows us to ensure that end testing service standards delivered by us are as per the parameters followed in our industry sector.
What does Relay Testing include?
Visual and Mechanical Inspection:
Relays are inspected for physical damages & compliance with specifications
Inspect cover glass, cover gasket, presence of foreign material, condition of spiral spring, moisture, disc clearance, rust and contacts
Check mechanically for freedom of movement, tightness of mounting hardware & tap screws and proper travel and alignment
All settings shall be made in accordance with customers
Perform following tests on nominal settings
Pick up parameters on each operating element
Timing test to be performed at three (3) points on time dial curve
Pick up target & seal in units
Special test as required to check operation of restraint, directional as well as other elements per manufacturer's instruction manual.